The ALIZÉ HYGRO TEMPO (HTC) grille provides a modulated flow according to the ambient relative humidity of the room and a timed complementary flow (30 minutes) whose opening is controlled by the user.
The vent can be mounted in a wall or ceiling position, in compliance with the following requirements:
In the wall position, the vents are mounted by a simple interlocking system on a Ø 125 mm duct or on a Ø125 mm sleeve to be sealed. The lip seal provides retention and sealing.
On the ceiling, the implementation can be carried out using a drywall 3-claw adapter sleeve or a Ø125 mm through-slab sleeve.
The vents have 3 fixing holes. It is advisable to screw the vents to the wall or ceiling using the 3 holes provided for this purpose. The electric vents must be fixed.
The vents have a cable grommet for the power supply and for the push button. See diagram opposite.
In the case of ceiling mounting, it is necessary to use an angle piece to guide the cord.
It is advisable to screw the grille support plate to the wall or the ceiling using the 3 holes provided on the plate.
We have a real identity that guides our actions on a daily basis and that irrigates our choices for more than 60 years now.
We are fully mobilized to keep our promises to our customers and stakeholders.
What is invisible is often what is most valuable. We are “wellness manufacturers”. We design products that improve living conditions.