ALIZÉ extract vents with airflow modulation for the tertiary sector provide a permanent fixed airflow, and for some, an additional airflow (under 80 Pa) that is timed or not controlled by a push button or switch (230 V air vents).
Mounting can be done in a wall or ceiling position, in compliance with the following requirements:
In the wall position, the vents are mounted by a simple interlocking system on a Ø 125 mm duct or on a Ø125 mm sleeve to be sealed. The lip seal provides support and sealing.
On the ceiling, the implementation can be carried out using a drywall 3-claw adapter sleeve or a Ø125 mm through-slab sleeve.
The vents have 2 fixing holes.
It is advisable to screw the vents to the wall or ceiling using the holes provided for this purpose. The electric vents must be fixed.
The vents have a cable grommet for the power supply.
The 230 V~ supply to the vent must be provided by a cable
2 wires (2 x 1.5 mm²) that must be built in and must come out at the rear of the support plate. This power supply must include a suitable protection device identified on the electrical panel in order to be able to carry out interventions on the vent.
Class II electrical appliance.
It is imperative to screw the vent on the wall or the ceiling using the 2 holes provided
on the plate.
We have a real identity that guides our actions on a daily basis and that irrigates our choices for more than 60 years now.
We are fully mobilized to keep our promises to our customers and stakeholders.
What is invisible is often what is most valuable. We are “wellness manufacturers”. We design products that improve living conditions.